Type THHN/THWN-2 building wire is intended for general purpose applications as defined by the National Electrical Code (NEC). Type THHN-THWN-2 is permitted for new construction or rewiring for 600-volt applications. Applications requiring Type THHN or THWN-2, the conductor is appropriate for use in wet or dry locations at temperatures not to exceed 90°C or not to exceed 75°C in oil or coolants. Applications requiring Type MTW conductor is appropriate for use in dry locations at 90°C, or not to exceed 60°C in wet locations or where exposed to oils or coolants. Applications requiring Type AWM conductor is appropriate for use at temperatures to not exceed 105°C in dry locations.
Nylon outer jacket for easy pulling. VW-1 rated 14 AWG - 8 AWG. All sizes are rated gasoline and oil-resistant II.
- Underwriters Laboratories Standards UL-83, UL-1063, UL-758
- AWM Spec 1316, 1317, 1318, 1319, 1320, 1321
- ASTM Stranding Class B3, B8, B787
- Federal Specification A-A-59544
- Canadian Standards Association C22.2 No. 75
- NEMA WC70/ICEA S-95-658
- Institute of Electrical and Electronics Engineers
Number of Strands: 19
Cross Section Area (mm2): 107.00
PVC Insulation Thickness (Conductor): 1.270 mm / 0.050 inches
Nylon Jacket Thickness: 0.180 mm / 0.007 inches
Outside Diameter: 15.85 mm / 0.624 inches
Weight: 0.731 lbs per ft
Allowable Ampacity: 195 Amps at 60ºC / 230 Amps at 75ºC / 260 Amps at 90ºC